LG UT24H.NN1 User Manual – Page 9
Posted on 22 Sep, 2019
Category: Air Conditioners
Product: LG UT24H.NN1
File size: 5 MB
The indoor unit installation
• Open the control box cover and connect
the Remote controller cord and Indoor
• Remove the control box cover for
electrical connection between the indoor
and outdoor unit.
• Use the cord clamper to fix the cord.
Control box cover
(On which the Electric
Wiring Connection is put)
between the indoor unit
and the outdoor unit
If the supply cord is damaged, it must be replaced by a special cord or assembly available from the manufacturer of its service
3.5 / 5.0 / 6.0 / 7.0
NORMAL CROSS-SECTIONAL AREA
The power cord
connected to the outdoor unit should be complied with
the following specifications (This equipment shall be provided with a
cord set complying with the national regulation).
The connecting cable
connected to the indoor and outdoor unit should
be complied with the following specifications (This equipment shall be
provided with a cord set complying with the national regulation).
Precautions when laying power wiring
Use round pressure terminals for connections to the power terminal block.
When none are available, follow the instructions below.
• Do not connect wiring of different thicknesses to the power terminal block. (Slack in the power
wiring may cause abnormal heat.)
• When connecting wiring which is the same thickness, do as shown in the figure below.
Make sure that the screws of the terminal are free from looseness.
The Power cord connected to the unit should be selected according to the
Round pressure terminal